Brought to you by
Brought to you by
Every house that is occupied by humans requires fresh air.
⇒ Therefore, home ventilation with heat recovery is indispensable in new constructions and in energy efficient refurbishments – see also our article about home ventilation.
The supply air coming from the heat recovery device can also transport a small quantity of heat. Just 10 W/m² of fresh air that is indispensable for hygiene can be provided for the supply air rooms (see heat capacity of fresh air). In a Passive House, the heating power requirement is extremely small - so small that it can be met by the 10 W/m² provided by a supply air heating system.
This makes it possible to develop convincingly simple building services systems for Passive Houses: “heating via ventilation systems”, without the need for additional ducts or larger ducts. If supply air heating and hot water provision is integrated into the same ventilation unit, we have a compact ventilation unit: heating, ventilation and hot water generation in one. Various solutions are possible for generating heat:
The amount of residual heat in the exhaust air of a home ventilation unit, also known as “enthalpy”, isn't particularly high, and condensing moisture contained in the air accounts for a large part of it. However, in a Passive House, the heat requirement is so small, that it can be covered almost completely by this residual exhaust air enthalpy. This concept was first published in 1995 by Wolfgang Feist. This facilitated the use of the Compact heat pump unit in Passive Houses.
Today, an increasing number of manufacturers offer such compact ventilation units. These units are highly efficient, as proven by scientifically evaluated measurements in Passive House housing developments.
|The “classical” compact heat pump unit combines heating,
ventilation and hot water generation in one easy to handle
unit; everything revolves around air: it acts as the transporting
medium for the heating and at the same time serves as the
source of heat (on the exhaust air side) for the heat pump.
An Energy balance can show whether such a compact unit is
adequate for heating a building.
Of course, not only Passive Houses can be heated using biomass. However, the available potential of sustainably-produced fuel is limited. In case of poor efficiency, only a fraction of the buildings in Europe (and also worldwide) can be sustainably supplied with biomass. However, if the level of efficiency is high enough, as it is in the Passive House for example, then the amount of fuel provided by sustainable agriculture and forestry is sufficient to cover a considerable share of the energy demand.
A high level of efficiency also benefits the user. If the required heating power is only between one and two kilowatt, it can be covered by the biomass heating device, a small box which doesn't require much space but can heat the whole house. This has a number of advantages:
The biomass heating device runs completely automatically, just like modern heating systems. Only a few kilogrammes of pellets for fuel are required per day. Not much space is needed to store this – it would even be possible to get the small amount of fuel along with the weekly shopping. The necessary combustion air can be drawn in with the fresh air by the compact unit. The very small volume flow rates of exhaust air can be extracted by the heat recovery system of the compact unit together with the exhaust air; there is no need for a separate chimney or flue pipe. Hence, the result is a simple building services concept for the Passive House based completely on renewable energy sources, that is still being developed and unfortunately is not yet available on the market.
There are already some Passive Houses in which heat is mainly generated by using a standard wood-pellet stove (Passive Houses Friedberg).
the main heating system
in a Passive House
in Friedberg, Germany
the fully automatic
stove also provides
in the summer,
round off the concept:
the stove doesn’t
have to be
Every user of gas stoves knows that even with a low output, heat generation is possible with gas. In spite of that, it took a long time before this technology could be used for post-heating in Passive House compact units. The advantages are obvious:
Compact ventilation units are not the only building services solution for Passive Houses: concepts based on natural gas are just as attractive as wood-pellet stoves or innovative electrical systems. Particularly those systems which combine solar thermal collectors are very effective. Efficiency technology and renewable energy complement one another ideally: with the low consumption of the Passive House, meeting most of the requirement through solar energy becomes possible.